Horn Strobe Alarm | Fire Alarm System | Alarm Bell | Bell & Indicating Lamp | Alarm Kebakaran | Tanda Kebakaran | Alarm
|Cara Pembayaran||Transfer Bank (T/T), Tunai|
|Kemas & Pengiriman||Unit / pcs - Paket Pekerjaan Proyek di lokasi Gedung|
|Negara Asal||Amerika Serikat|
Horn Strobe Alarm
* The horn strobe shall be wired as a primary-signaling notification appliance and comply with the Americans with Disabilities Act requirements for visible signaling appliances, flashing at 1Hz over the strobe’ s entire operating voltage range.
* The strobe light shall consist of a xenon flash tube and associated lens/ reflector system.
* The strobe shall be powered independently of the sounder.
* The horn shall have three audibility options and an option to switch between a temporal three-pattern and a non-temporal ( continuous) pattern.
* The horn on horn strobe models shall operate on a coded or non-coded power supply.
* The horn strobe shall be listed to UL 1971 and UL 464 and shall be approved for fire protective service.